Running a little low on poles within this sub panel. Wanted to double check, get a little consensus if this wiring sounds right. The goal is to plug in 4x 220v 1kw lights.
30 amp dual pole breaker. Romex 10-2 from breaker into a junction box , 2 runs of Romex 12-2 pig tailed to the 10-2 in the junction box. Each lead of 12-2 will lead to a 20a duplex 220v outlet.
Could do the pig tailing within a double gang box, but I feel like using a junction box would be cleaner, less crammed, easier access to the connection.
Anyone notice anything wrong with this set up?